Texas Administrative Code
|TITLE 16||ECONOMIC REGULATION|
|PART 1||RAILROAD COMMISSION OF TEXAS|
|CHAPTER 9||LP-GAS SAFETY RULES|
|SUBCHAPTER B||LP-GAS INSTALLATIONS, CONTAINERS, APPURTENANCES, AND EQUIPMENT REQUIREMENTS|
|RULE §9.134||Connecting Container to Piping|
LP-gas piping shall be installed only by a licensee authorized to perform such installation, a registrant authorized by §9.13 of this title (relating to General Installers and Repairman Exemption), or an individual exempted from licensing as authorized by Texas Natural Resources Code, §113.081. A licensee shall not connect an LP-gas container or cylinder to a piping installation made by a person who is not licensed to make such installation, except that connection may be made to piping installed by an individual on that individual's single family residential home. A licensee may connect to piping installed by an unlicensed person provided the licensee has performed a pressure test, verified that the piping has been installed according to the LP-Gas Safety Rules, and filed a properly-completed LPG Form 22 with LP-Gas Operations, identifying the unlicensed person who installed the LP-gas piping.
|Source Note: The provisions of this §9.134 adopted to be effective February 1, 2001, 26 TexReg 947; amended to be effective September 1, 2005, 30 TexReg 4810; amended to be effective February 1, 2008, 33 TexReg 122; amended to be effective December 24, 2012, 37 TexReg 9913|