Texas Administrative Code
|TITLE 16||ECONOMIC REGULATION|
|PART 1||RAILROAD COMMISSION OF TEXAS|
|CHAPTER 9||LP-GAS SAFETY RULES|
|SUBCHAPTER B||LP-GAS INSTALLATIONS, CONTAINERS, APPURTENANCES, AND EQUIPMENT REQUIREMENTS|
|RULE §9.135||Unsafe or Unapproved Containers, Cylinders, or Piping|
In addition to NFPA 58, §§188.8.131.52, 184.108.40.206, and 5.2.2 a licensee or the licensee's employees shall not introduce LP-gas into any container or cylinder if the licensee or employee has knowledge or reason to believe that such container, cylinder, piping, or the system or the appliance to which it is attached is unsafe or is not installed in accordance with the statutes or the LP-Gas Safety Rules.
|Source Note: The provisions of this §9.135 adopted to be effective February 1, 2001, 26 TexReg 947; amended to be effective September 29, 2003, 28 TexReg 8318; amended to be effective February 1, 2008, 33 TexReg 122|