Texas Administrative Code
|TITLE 16||ECONOMIC REGULATION|
|PART 1||RAILROAD COMMISSION OF TEXAS|
|CHAPTER 9||LP-GAS SAFETY RULES|
|SUBCHAPTER B||LP-GAS INSTALLATIONS, CONTAINERS, APPURTENANCES, AND EQUIPMENT REQUIREMENTS|
|RULE §9.137||Inspection of Cylinders at Each Filling|
In addition to NFPA 58, §§18.104.22.168, 22.214.171.124, and 5.2.2 before filling a container or cylinder, the individual filling the container or cylinder shall conduct a visual inspection of the exposed, readily accessible areas of the container or cylinder for any obvious defects. Where the container or cylinder is dented, bulged, gouged, or corroded such that the integrity of the container or cylinder is substantially reduced, such container or cylinder shall not be filled.
|Source Note: The provisions of this §9.137 adopted to be effective February 1, 2001, 26 TexReg 947; amended to be effective September 29, 2003, 28 TexReg 8318; amended to be effective February 1, 2008, 33 TexReg 122|