Texas Administrative Code
|TITLE 16||ECONOMIC REGULATION|
|PART 1||RAILROAD COMMISSION OF TEXAS|
|CHAPTER 9||LP-GAS SAFETY RULES|
|SUBCHAPTER D||ADOPTION BY REFERENCE OF NFPA 54 (NATIONAL FUEL GAS CODE)|
|RULE §9.306||Room Heaters in Public Buildings|
In addition to applicable requirements in NFPA 54, §10.22.3, Installation of Specific Appliances, room heaters in schools, day care centers, foster homes, hotels or other similar buildings or rooms used for temporary lodging shall be vented and equipped with a safety shut-off device, except that room heaters with 40,000 Btu or less input and infrared heaters are not required to be vented, but shall have a safety shutoff device and an oxygen depletion system (ODS).
|Source Note: The provisions of this §9.306 adopted to be effective February 1, 2001, 26 TexReg 947; amended to be effective February 1, 2008, 33 TexReg 122; amended to be effective January 6, 2020, 45 TexReg 127|